Contact Person : Dina Huang
Phone Number : 18761502682
WhatsApp : +8618761502682
December 24, 2021
【Abstract】The AFPM100/B1 monitoring equipment adopts a wall-mounted structure, adopts a centralized and modular design, and has the characteristics of strong functions and flexible settings. The system adopts an 8-inch industrial tablet computer, adopts the Windonws XP system, and can support AFPM100 fire protection equipment power monitoring software. The printer can print all alarms, faults and various operations of the Chinese character information of the system, and has multiple functions such as management, viewing, alarming, printing, and so on.
GB28184-2011 "Fire-fighting equipment power supply monitoring system" has clearly included the fire-fighting equipment power supply monitoring system into the building fire protection regulations, and compulsorily stipulates the basic functions of the fire-fighting equipment power supply monitoring system. Therefore, this article explains the scope of application and functions of the power supply monitoring system for fire-fighting equipment.
[Keywords]: AFPM100/B1; fire-fighting equipment power monitoring equipment; AFPM3-2AVM
With the rapid development of society, there are more and more modern large-scale buildings, public gathering places and first-class high-rise buildings. The fire control room controls the automatic alarm system, automatic spray system, fire accident broadcasting system, smoke prevention and exhaust system, Operation of multiple systems such as gas fire extinguishing system, fire hydrant system, emergency lighting system, etc. Whether the fire alarm system in the fire control room and the related fire-fighting linkage equipment can work normally depends on the working state of the power supply of the fire-fighting equipment. Therefore, in the event of a fire, if the power supply of fire-fighting equipment cannot work reliably and stably, the fire-fighting facilities that have invested a lot of money may be in vain. In recent years, fire-fighting equipment malfunctions due to the out-of-control power supply of fire-fighting equipment, leading to fire spreading accidents have been common.
1. Project Introduction
An industrial park in Suzhou is a strategic emerging industry project of the Suzhou Municipal Government. It is a focus camp for entrepreneurial enterprises and large emerging industries, and a new entrepreneurial cultural industry park.
1.1 User needs
①The function of monitoring host for power supply of fire-fighting equipment
l The monitoring equipment should be able to receive the monitoring alarm signal from the fire-fighting equipment power monitoring detector, and send out sound and light alarm signals within 10s to indicate the alarm position, display the alarm time, and keep it until the fault is eliminated.
l Equipped with muffler and muffler indication function, when there is an alarm or failure, the sound signal can be restored to output, which is convenient for on-site debugging and maintenance
l The monitoring equipment should have at least two levels of operation. The duty officer is only allowed to eliminate the sound alarm signal and query information. The key or password should be used to enter the operation level above the operator. The key or password used to enter the high operation level can be used to enter the low operation level, but the key or password used to enter the low operation level cannot be used to enter the high operation level.
③Easy to operate and maintain
l The operation page adopts a graphical display mode, which intuitively shows the working status of the power supply of each fire-fighting equipment, the operation interface is simple and convenient, the software runs stable and reliable, and has good scalability and maintainability.
2. Introduction to Field Project Application Products
AFPM100/B1 fire-fighting equipment power supply monitoring system
The AFPM fire-fighting equipment power monitoring system is a computer measurement and control system that integrates monitoring, alarm and management independently developed by Acrel. This system can be widely used in intelligent buildings, high-rise apartments, hotels, restaurants, commercial buildings, industrial and mining enterprises, petrochemicals, culture, education, health, finance, telecommunications and other fields (hereinafter referred to as monitors). The AFPM100/B1 fire-fighting equipment power supply status monitor is the core of the AFPM fire-fighting equipment power supply monitoring system.The AFPM100/B1 monitor is connected to multiple sensors through two buses to form a distributed fire-fighting equipment power supply monitoring system, which monitors the working status of the main and backup power supplies of the fire-fighting equipment in real time.The monitor adopts a centralized and modular design and is equipped with sensors,and monitor,store,analyze informations like operation information, fault alarm information of the voltage, current, switch status of fire equipment,so that it can be convenient for users to monitor and manage.Not only that the monitor can also collect and display the data of the power supply of fire fighting equipment by human-computer interaction interface,with functions such as management, viewing, alarming, and printing.This equipment has reasonable structure, high reliability, strong function, convenient maintenance, high cost performance, friendly system interface, easy to learn and use.
The AFPM fire-fighting equipment power monitoring system is composed of AFPM100/B1 fire-fighting equipment power monitoring equipment, voltage/current sensors, AKH series current transformers and other accessories. Each device of the system is connected by two buses, and the construction and wiring are simple and convenient.
AFPM100/B1 fire-fighting equipment power supply monitoring equipment
2.2.1Panel component layout and function description
1. Running indicator light (green), the light is always on when the monitor is running
2. Power indicator light (green), when the power supply is normal, the indicator light is always on, and it flashes when the main and backup power fails
3. Silence indicator light (green), when the monitor is in silence state, the indicator light will be on, otherwise it will not light up
4. System failure indicator (yellow), when the monitor system fails, the indicator lights
5. Other fault indicator lights (yellow), when the monitor receives other fault signals, the indicator lights up
6. Reset button (black) to reset the system
2.2.2 Technical parameter
2.2.3Internal terminal wiring table
Wiring terminals for power monitoring system of fire-fighting equipment
Table 2 AFPM100/B1 internal wiring table
2.3 AFPM3-2AVM type voltage sensor
2.3.1 Product appearance
2.3.2The function of AFPM3-2AVM series voltage sensor:
The sensor has 2 three-phase voltage detection functions;
l The sensor supports 2-channel linkage signal input function (2-channel passive dry contact input, input mode: built-in power supply);
l The sensor supports 1 relay output function, the contact capacity is AC220V/1A, DC30V/1A;
l The sensor has multiple protection functions such as overvoltage, undervoltage, and error;
l The sensor has an event storage function, which can record the time, type, and parameters of the alarm, and can analyze the on-site situation according to the alarm record;
l Communication method: two-bus communication.
2.3.3 technical parameter
2.4 AKH-0.66 I type current transformer
2.4.1 Product appearance
3 Field Application
3.1System network diagram
3.2 System software running interface
Main interface of system operation Condition monitoring interface
Contains three parts: "software title area", "function list area", and "page display area". You can enter each related function interface by clicking the button in the "function list area".
It is used to set parameters internally, measure parameter status parameters, and remotely release alarms or open and close the monitoring device on this interface.
Device detection interface Event logging interface
This detection function is an operation function that can be performed by "administrators" and "operators", and is mainly used for equipment self-checking and manual detection of indicator lights on the panel of the monitoring system.
In this interface, the user can query the records of the corresponding alarm or action type in any period of time, and all levels of operation authority can view the information of this interface.
3.3 Equipment field application photos
The AFPM fire-fighting equipment power monitoring system can effectively reduce the failure rate of the power supply of fire-fighting equipment and ensure the normal operation of fire-fighting equipment, thereby providing strong technical support for the normal operation of fire-fighting equipment, evacuation and rescue of personnel in the event of a fire.AFPM fire-fighting equipment power monitoring system will "escort" fire-fighting equipment,and play an effective role in protecting people's lives and state property.
. Zhong Chou. The application of electric power meters in the sub-item measurement of electric energy in large public buildings[J]. Modern Building Electric 2010.6
. Acrel Co., Ltd. Product Selection Manual. 2018.01
. GB50116-2014 Code for fire protection of building design[S].
. GB28184-2011 Fire-fighting equipment power supply monitoring system[S].
Enter Your Message